Conventional Fire Alarm Control Panel with sixteen Zones
Key Specifications/Special Features
•Sixteen Style B (Class B) Initiating Device Circuits (IDCs).
•All zones accept two-wire smoke detectors and any normally-open contact devices.
•Four built-in, Style Y (Class B) Notification Appliance (Signal) Circuits (NACs).
•Alarm, Trouble and Supervisory, Form-C relays standard.
•Resettable four-wire smoke detector power @ 500 mA.
•Non-resettable power @ 500 mA.
•One-man walk-test programmable for silent or audible test.
•Disable/Enable control per IDC.
•Reverse polarity protection.